Installation Clearance - Fire Deck Series (6045 to 8645)
The Wood Stone Fire Deck oven must have a minimum 1'’ (25mm) clearance to combustibles from all sides, and 24" (610mm) clearance to combustibles from the top. If building materials will contact the oven, they must be completely noncombustible.Please note that standard dry-wall (or sheet rock) is considered a combustible. When non-combustible building materials contact the body of the oven, the respective clearances are transferred to those non-combustibles.
- Any facade above and/or 6" (150mm) to either side of the oven doorway, must be constructed of non-combustible building materials.
- Install this oven only on a non-combustible floor surface. The non-combustible floor surface must extend 36" (920mm) out in front of the oven, and extend 30" (775mm) to either side of the oven doorway.